- Attic Fans
- Ceiling Fans
- Central Vacuum System
- Floor Heating
- Snow Melting Systems
- Circuit Breaker
- Electrical Wiring
- Smoke Detectors
- Carbon Monoxide Detector
- Surge Protection
- Indoor Lighting
- Outdoor Lighting
- GFCI Outlet Installation
- Flat Screen TV Installation
- Home Automation
- Home Theater Installation
- Home Theater Repair
- Computer Wiring
- Pool and Hot Tub Wiring
- Vehicle Charging Stations
Why are half of my lights out and large appliances not working?
Check for tripped breakers and reset your main breaker. If the main breaker is warm to the touch, call a qualified, licensed electrician immediately. If resetting the breaker does not fix the problem, it is possible you have lost one phase (leg) of your main power supply. Contact your utility company and have them inspect their service line for problems
Christmas light problems
At Christmas time, we receive numerous calls regarding electrical problems with the bathroom, garage or outdoor outlets not working. The usual cause for this problem is that the outdoor Christmas lights have tripped a GFI outlet or circuit breaker in your home. Standard circuit breaker will trip if you over load the wiring with too many lights on one breaker. GFI circuits are a little bit different. Morning dew, rain, or a sprinkler may introduce a bit of moisture into the Christmas electrical plugs and this could result in a ground fault. Weather proofing or covering of the electrical outlet and plug connections should reduce nuisance tripping of the GFI protection device.
How to check it out: First, unplug the outdoor lighting. Second, go to the electrical panel, check the circuit breaker and reset it if needed. Now, test the outlet for power. If it’s working, allow time for the wiring to dry out and reconnect your lights. If the breaker trips again, call an electrician to fix the problem.
GFI outlets are outlets with the little test and reset buttons in them. Many times, the GFI outlet in a bathroom or garage that feeds power to the outdoor outlet has tripped because of a wet plug on the holiday lights. Now, what to do: First, unplug the outdoor lighting. Second check all the GFI outlets by pushing the test and then the reset buttons. Check for GFI outlets in the bathrooms, basement, garage and the outdoor outlets themselves. Now test the outlet for power. If it’s working, allow time for the wiring to dry out and reconnect your lights. If the GFI outlet trips again, call an electrician to fix the problem.
What is a GFCI?
A ground fault circuit interrupter, or GFCI, is a electronic devices for protecting people from serious injury due to electric shock.
Why is my smoke detector chirping intermittently?
Usually when a smoke detector is chirping intermittently, it is signaling the need to replace the back-up batter. If replacing the battery in your smoke detector does not eliminate the chirping, call a qualified, licensed electrician.
What can I do to protect electrical equipment for lighting damage?
Surge suppression devices can be installed in the main service and sub-panels by a qualified electrician. These devices, in addition to point of use surge suppression, offer the best protection from power surges associated with lightning. These devices are typically sacrificial and may require replacement if they experience a lightning strike.
I replaced the lamp in my recessed light and it blinks on and off. What’s wrong?
Most recessed light fixtures contain a thermal cutoff device that de-energizes the lamp if temperatures exceed the rating of the housing. This commonly occurs when a lamp is replaced with one of a higher wattage. When the temperature within the fixture cools, the thermal will reset and the lamp will come back on. Installing the correct wattage lamp for the fixture will cure this.
My clothes dryer stopped producing heat.
This is usually caused by a defective 240-volt circuit breaker. Probably, one side of the breaker has gone bad. Replacing the breaker will fix this problem, provided that no damage has occurred on the breaker panel contact, also known as the buss bar, due to a loose connection on the circuit breaker.
Does my whole house need to be rewired if I have aluminum wiring?
No. A Licensed Electrician can fix all the connections where aluminum wiring connects to receptacles, switches, light fixtures, etc., and this will prevent any problems.
When is it time to call an electrician?
Any time you need indoor or outdoor electrical work done, that’s the time to call on a professional, licensed electrician. What might seem like a simple situation to you might actually be a potential danger. Most electrical fires occur because a homeowner didn’t think there was a serious problem. Here are some situations where it would be wise to call an electrician:
- You need to upgrade your service.
- Your lights are dimming and flickering.
- You need to add some additional outlets.
- You have power surges when the refrigerators kicks in.
- You keep tripping a circuit breaker or blowing a fuse.
- Any time something unusual is happening with your electrical system.
A receptacle in my bathroom, kitchen or elsewhere stopped working. Why?
Check the receptacle; if it is a GFI, it may be tripped. These are the receptacles with a reset button on them. The receptacle may need to be reset. It is possible in an older home to find that the GFI receptacle in the garage is also protecting a second floor bath, so check carefully.
My house has aluminum wiring. Is it dangerous?
Aluminum wiring (instead of copper) became quite popular during the 1970s, and was extensively used. Since that time, aluminum wiring has been implicated in a number of house fires, and most jurisdictions no longer permit it in new installations. We recommend, even if you’re allowed to, that you do not use it for new wiring. But don’t panic if your house has aluminum wiring. Aluminum wiring, when properly installed, can be just as safe as copper. Aluminum wiring is very unforgiving of improper installation.
I plug my hair dryer in in the bathroom and when the air conditioner is on in the bedroom the breaker trips. Why?
This type of problem, common in older homes, is due to overloaded circuits. The best solution is to run new circuits to the appliances that require more current. In this example a new 20-amp circuit for the bathroom and new circuit for the air conditioner would be a good solution.
A light fixture in my house is flickering. What should I do?
A flickering light could be the symptom of several problems. This should be checked. It could be a loose connection in the circuit. It could also be a problem outside your house, especially if all the lights in the house seem to be flickering. In any case like this, it’s best to not use the lights and call a licensed electrician to check it out.
Why do I need so many receptacles on my kitchen counter back splash?
In a kitchen, the code requires that no point along the counter top be more than 24” from an outlet. Also, any counter of 12” or more requires a receptacle. These receptacles must all be GFI protected.